Federal Construction Group, Inc. is tasked to:
a) Install three new blue strobe lights for AFFF release in Hanger Bay area. One strobe on east west, and north wall.
b) Reprogram AFFF Abort switches for release. Any switch from any station shall abort the AFFF release per UFC
c) Make signs for each AFFF Release/Abort station. Sign should notify occupant of the zone that the Release/Abort
station is connected too. Six sign in total, two for zone #1, one for zone #2, one for #3, and two for zone #4. All
signs should be made in accordance with UFC and NFPA.
d) Hanger bay shall be marked in red lettering on the wall (20-30ft height) the zone for AFFF release, per the UFC
and Hanger Deck.
e) Hanger bay shall be marked in red lettering on the wall (20-30ft height), “No Open Flame Permitted” per the
UFC, NFPA and StaO 11320.
f) Install cover for control unit for inverter valve for AFFF release on the east wall.
Bldg 410, 78 and 80
a) Remove existing Filter in the VESDA type systems (8 filters) Installation
b) Install new filters for VESDA system (8 filters) and test system pre NFPA and UFC.
Bldg 78, 80, 95,101,146, 220, 227, 530, 634, 635, 965, 1521, 1700, 3216, 6004
a) Remove existing packing and bolts for fire pumps (26) Installation
a) Install new packing and bolts for fire pumps (26) per UFC and NFPA
Bldg 78, 80, 101, 103, 109, 220, 227
a) Remove batteries past the five install date (20). Installation
a) Install new batteries (20).
a) Remove circuit breaker isolation switch in pump controller #2 Installation
a) Install new circuit breaker isolation switch in pump controller #2.
a) Install 200 gallons of AFFF to Main AFFF Tank.