Federal Construction Group installed new 60′ Class 3 power pole with crossarms, buckarms and insulators. intercept overhead 12 KV conductors and extended to the new transformer power pole. We also provided (1) each 45′, Class 1, (3) each/single transformer pole mounted with crossarms, insulater, (3) 50 KVA, 12 KV-120/208VAC, (3) fused cutouts, lighting arresters, (1) #1/0 ground with PVC cover to 3/4″ x 10′ cu clad steel ground rod and down guy.
Federal Construction Group provided 400 A WP, 120/208 V, 3P, 4W main panel with 400 A main circuit breaker and (4) 100A branch circuit breakers to feed (4) 100A disconnect switches, (4) 60A circuit breakers to feed (4) 30 A disconnect switches all WP mounted on unistrut complete with NEC sized copper wiring in wireways. All disconnect switches were non-fused type. We provided 1 #1/0 CU ground wire to 3/4″ x 10′ ground rod. All power outage was coordinated with base High Voltage electrician.