Federal Construction Group, Inc. is tasked to provide all personnel, equipment, tools, materials, technical supervision and other
items and services necessary to perform: inspection, abatement, installation and repair to all items
within this SOW.
The contractor shall notify the Project Manager and building personnel before start of work and upon
All newly repair and or installed items shall be complete and useable upon completion of work.
The contractor shall cleanup work site and dispose of any discarded material off station.
Scope of Work:
a) Remove sprinklers heads in lobby area.
a) The lobby for Bldg. 1058 was recently remodeled and a new exit was installed at the west end
of the lobby. This marked exit does not have a manual pull station installed near it as required. Install
the required manual pull station.
b) Install new sprinklers and piping for new lobby lay out in accordance with NFPA and UFC.
a) Install exit sign above exit door in the exceptional family office. Training area converted to an
office area needs to have exit light installed above door.
a) Contactor shall remove two horn/strobes in theatre seating area.
a) Contactor shall install two news horn/strobes in the theatre seating area.
b) Contactor shall add one new horn/strobe in lobby
c) Contactor shall add one new horn/strobe in upstairs film room.
a) Fire Alarm system voice needs to be changed to a female voice instead of a male voice in
accordance with NFPA and UFC.
b) Notification devices in Rm 1117, 1118 and outside west side not working. Repair or replace
c) Devices in building are not synced, sync devices in accordance with NFPA and UFC.
a) Remove underground fiber optic line for Fire Alarm system.
b) Install new underground fiber optic line in accordance with NFPA and UFC.
a) Install new notification device in basketball court area.
a) Remove pull station in test cell area.
a) Install new pull station in test cell area in accordance with NFPA and UFC.
a) Remove pull station and beacon in test cell area.
b) Remove batteries and power charger in FACP.
a) Install new pull stations and beacons in test cell area.
b) Install new batteries and power charger for FACP.